Pro HVAC company Southern Comfort Mechanical says on its blog, “If there’s mold growth inside the handler due to excess moisture, algae in the condenser drain line or a dirty evaporator coil, it can negatively impact your AC unit’s efficiency. The filters inside may also build up excess dirt and become clogged, which will also make your AC [or heat pump] waste energy trying to sustain the cool climate inside your home.” These issues are easy to solve. They don’t require replacing the air handler.
Brands like American Standard, Trane and Lennox cost the most. Goodman is the cheapest. The rest populate the middle of the spectrum. Here’s something to know: The quality among brands isn’t as great as price differences. The difference in prices reflect that some customers want “bargain” equipment to save cost and others want “premium” equipment they believe will run longer with less trouble. Therefore, each manufacturer has priced to meet consumer perception.
One of the best ways to know if your ducts or vents need to be cleaned is to just check them. Your eyes will be able to check for indications of mold, dust or pollen buildup. You might also be able to smell the presence of mold, which would be a clear indicator. Ductwork will have some buildup of dust, since the return registrars pull air back in. However, this doesn't mean your ducts have too much debris, and you can easily clean them with a duster or vacuum.
Alberto said they were busy but could either install on the upcoming Saturday. We were going to be out of town and said unfortunately that day did not work. He then proposed the upcoming Tuesday as a possible solution, but just had to confirm with another appointment. I said great. I will review the estimate and call your office to confirm I want to move forward with the install.
The original furnace was a coal fired “octopus” design which had no blower to circulate the air but relied upon warm air rising to distribute the heat. That also means that the system breathed air in from the basement and most of this type did not have a cold air return system. At some point (probably in the 1940’s) the system was upgraded to a forced air gas furnace. The upgrade included replacing the 12″ diameter air ducts exposed in the basement with 6″ ducts and a cold air return system of ducts from the two (only two) air returns on the first floor.
I have worked cleaning HVAC in my area for almost 5 years. I always do a thorough inspection and cleaning, providing before and after photos. I have completed some jobs where I felt that it was not entirely necessary, but ultimately what the customer wanted. With that being said, I have endless photos of unspeakable horrors. Hotels are usually nasty, post construction mess is certain, pets and kids create lots off debris, bugs congregate and die, then spiders set up and die, I have even had one supply that was nearly plugged with sand!
"Customer service was great, and the price was in-line with other places, and fast service. We had a whole replacement of the outside and inside. I would have liked to see a better install for the furnace and new thermostat - the new thermostat should have gone where the old one was, and even tho the new furnace was a tight fit, they didn't offer to come back and repair the case molding, or give me a discount on the damage done, and I believe they should have put a disconnect box on the outside of the home, to make it easier for any future repairs needed. Other than that, am very happy with the cooling and heating!"